San Jacinto Plumbers
Serving Residential & Commercial Clients Since 1978
For nearly 4 decades, Schuelke Plumbing has served homeowners and business owners in the Inland Empire. We have extensive experience handling a variety of large and small plumbing issues, and will work hard to leave your home or business functional. Plumbing problems are not only inconvenient, but they also threaten the safety and well-being of your building. Our San Jacinto plumbers will work quickly to diagnose and fix the issue.
Contact us today to request a free estimate.
Save Water & Money with Our Water Conservation Solutions
Water conservation is important, especially in dry southern California. There are several things you can do to save water and lower your utility bills each month. You can take shorter showers, have leaky pipes repaired or replaced, set a time for sprinklers, run a dishwasher or load of laundry only when full, and instal low-flow shower heads and toilets.
Water bills can be expensive, especially during the warm summer months. Thus, it is important to pay attention to how much water you are using each month, and to make practical changes to eliminate wasted water.
Understanding the Benefits of the Aqus System
The Aqus System works by redirecting water from your sinks to your toilet cisterns. This means the excess water that you run down the sinks will be recycled to fill your toilet, helping you save up to 5,000 gallons of water each year. You will not only reduce water waste, but you will enjoy savings from lower water bills each month.
The Aqus System is designed for both residential and commercial buildings. It has even won awards for its efficiency and innovative design. Our team can install this cutting edge system to help your home or business save money and reduce water waste.
Experienced Plumbing Repair Services for Your Home or Business
Not only do we provide the latest technology and equipment to help you save money and eliminate water waste, but we also repair, replace, and install high quality plumbing systems to protect your home from water damage. If your drains are clogged or your water heater is experiencing issues, it is important to hire our team as soon as possible. We are available to handle emergency plumbing issues around the clock, even on holidays and weekends.
Got a Plumbing Problem? Call Schuelke Plumbing Today at (909) 280-4108!
At Schuelke Plumbing, we have decades of professional experience. If your plumbing system is experiencing issues, or you want to install a high quality water conservation system, we can get the job done quickly and efficiently. Our San Jacinto plumbers have a thorough and up-to-date knowledge of the latest plumbing technology. From repairing a clogged kitchen drain to repiping your entire building, we have the knowledge and skill to handle any issues that may arise. Trust our team to get the job done right the first time.
We are available around the clock for your convenience. Contact our office today to request an appointment.
Recent Jobs and Reviews in San Jacinto, CA
Job Locations and Reviews
Attempted to snake mainline from cleanout on side of office. Was un able to get clog cleared. After further inspection it appears the whole row of units are backed up. Attempted to clear clog from other cleanouts but was unsuccessful. Explained to customer that hydrojetting will need to be performed either via acess behind unit 277 or 275. Quoted 495 for first two hours. 195 for every hour after
Several units around 207 where clogged. Performed hydrojetting via cleanout behind unit 207 and was able to clear clog. Followed up with camera inspection and saw the claim sewer main had several low spots which I believe to be causing the clogs.
Was able to clear clog for unit 218. Performed camera inspection and saw customers sewer line where cleanout and sewer main connect has flattened causing issues with drainage. Recommended digging this section up and repairing to prevent further clogs. After clearing clog for 218 management explained that unit 266 was clogged as well. Removed clog and saw customer has large root intrusion which was the cause of the clog. Recommended digging this section up and repairing damaged section to prevent further clogs. After clearing these two clogs Maitnace notified me that several units around 207 where clogged as well attempted to clear clog but was unable to with my cable snake and recommend hydrojetting for 495.00
Customer has a offset and root intrusion on cleanout riser approximately 3’ deep. Recommended digging up cleanout and replacing damaged section of pipe. Upon exposing riser for cleanout we saw that riser had snapped off and separated from fitting of cleanout which was allowing the roots to enter nWe removed old riser and installed new riser and Jim cap. Performed camera inspection and didn’t see any further issues.
Customers 1” Watts pressure regulator had a pin hole leak it it. Shut water off to the house and replaced regulator. While working on regulator I noticed the 1” ball valve in front yard was not shutting off all the way. Recommended replacement of ball valve.
Performed camera inspection of sewer line via accessible cleanout for kitchen line located on side of the house as well as camera inspection of sewer main cleanout that was located in front yard. After performing inspection via main line cleanout I noticed customer has a root intrusion and offset at riser for the 3” cleanout. Recommend digging up this cleanout to remove damaged section of pipe and plumbing in new section in order to eliminate root intrusion. The rest of customers sewer main and kitchen drain appeared to be in good condition with no other issues.
Customer has water damage to ceiling and surrounding walls in living room under upstairs bathroom. Recommended performing proper mitigation to prevent further damage. Leak appears to be a drain issue. Once drywall is exposed we will be able to run test to determine what exactly is leaking. Once leak is identified we will be able to give separate price for repair
After performing leak detection I was unable to determine that there was any leaks on the water system. I listened to manifold and angle stops and could not hear anything. Checked meter for several minutes and meter was not moving which is a good indicator that there is not a leak on the water system. Inspected behind units bathtub via access panel. Noticed the drain basin was full of water. Ran water in the tub and immediately water started flowing out from the over flow. Replaced overflow drain and gasket to stop leak. Explained to manager to keep an eye on the unit and the moisture in the walls and carpeting in the bedroom continue then to let us know.
Customer had a hot water leak from water heater over to manifold behind shower valve. Instead of performing direct access repair we instead re routed the line over head. Customer had sever water damage that we recommended performing proper remediation
Customer had a hot water line leak in master bedroom near water heater. Instead of removing carpet and jackhammering flooring we performed re route of hot water line and tied back into manifold behind shower. Doing so eliminates hot water line that goes under ground from water heater.
Thank you very much for the great review. We love to hear that our customers are very satisfied with our work. Thank you for your business!